Hello everybody,
how can I solve the following problem using the "pressure drop and flow calculator"?
I have a water tank with a water column of 50 meter.
At the bottom of the water tank is a straight vertical pipe of 800 meter length with a diameter of 0.3 meter.
Now I want to calculate the flow rate.
The question is what to use as pressure (p1p2). Do I have a total water column of 850 mWS (50 mWS in the tank + 800 mWS in the vertical pipe) or is it just 50 mWS? Can I use the calculator?
If for example the total water column would be 50 mWS. Would than p1 =50 mWS and p2=0 mWS
Looking forward for any answers! Thank you very much
Pressure in a vertical pipe

 Posts: 57
 Joined: Sat Sep 17, 2011 8:50 am
Re: Pressure in a vertical pipe
If the tank is open to atmosphere your p1=0.
But as you do not have option to enter height in calculator, you can enter 50 + 800 mWS as p1. p2 = 0.
Also you have K1 = 0.5 (pipe entrance) and K2 = 1 (pipe exit) with total of K1 + K2 = 1.5 total resistance coefficient.
Hope this helps!
But as you do not have option to enter height in calculator, you can enter 50 + 800 mWS as p1. p2 = 0.
Also you have K1 = 0.5 (pipe entrance) and K2 = 1 (pipe exit) with total of K1 + K2 = 1.5 total resistance coefficient.
Hope this helps!
Pipe flow calculations  free fluid flow calculators
Re: Pressure in a vertical pipe
It helps a lot. Thank's!
How did you receive the values for K1 and K2?
Regards
How did you receive the values for K1 and K2?
Regards

 Posts: 57
 Joined: Sat Sep 17, 2011 8:50 am
Re: Pressure in a vertical pipe
You can find also K  resistance factor calculator there
Pipe flow calculations  free fluid flow calculators
Return to “Flow calculators and fluid flow problems”
Who is online
Users browsing this forum: No registered users and 2 guests